Surge protective devices (SPDs) are designed to meet requirements for UL 1449 Forth Edition and IEC/EN 61643-11. They are DIN-rail mountable featuring a fail-safe protection, visual indicator and remote signal contact. It has a good environmental adaptability and meets the requirements of high reliability in important field.
8/20 Current Impulse
Current impulse with a nominal virtual front time of 8 µs and a nominal time to half-value of 20 µs. ---- IEC 61643-11
1.2/50 Voltage Impulse
Voltage impulse with a nominal virtual front time of 1.2 µs and a nominal time to half-value of 50 µs. ---- IEC 61643-11
Maximum Continuous Operating Voltage
Maximum r.m.s. voltage, which may be continuously applied to the SPD's mode of protection. ---- IEC 61643-11
Nominal Discharge Current
Crest value of the current through the SPD having a current waveshape of 8/20 µs. ---- IEC 61643-11
Impulse Discharge Current for Class I Test
Crest value of a discharge current through the SPD with specified charge transfer Q and specified energy W/R in the specified time.
---- IEC 61643-11
Maximum Discharge Current
Crest value of a current through the SPD having an 8/20 µs waveshape and magnitude according to the manufacturers specification. Imax is equal to or greater than In.
Modes of protection
An intended current path, between terminals that contains protective components, e.g. line-to-line, line-to-earth, line-to-neutral, neutral-to-earth. ---- IEC 61643-11
Voltage Protection Level
Maximum voltage to be expected at the SPD terminals due to an impulse stress with defined voltage steepness and an impulse stress with a discharge current with given amplitude and waveshape. ---- IEC 61643-11
Short Circuit Current Rating
The suitability of an SPD for use on an AC power circuit that is capable of delivering not more than a declared rms symmetrical current at a declared voltage during a short circuit condition. ----UL 1449
Degrees of Protection Provided by Enclosure (IP Code)
Classification preceded by the symbol IP indicating the extent of protection provided by an enclosure against access to hazardous parts, against ingress of solid foreign objects and possibly harmful ingress of water. ----IEC 60529
A non-resettable device incorporating a THERMAL ELEMENT which will open a circuit once only when exposed for a sufficient length of time to a temperature in excess of that for which it has been designed. ----IEC 60691
Alloy Type Thermal-Link, Alloy is the thermal element.
● AC Power Supplies
● New Energy
● Residential Building
● Internet Data Center (IDC)
● Industrial Control
SETsafe | SETfuse Quality Policy
Provide Industry-Leading Products
Select critical raw materials: Must be from a manufacturer with quality management system (ISO9001, IATF16949) certification.